BSRIA document BG50/2013 ‘Water Treatment for closed heating and cooling systems’ states that ‘chemical dosing pots should remain open to the system with a continuous through flow of water’ viagra kaufen per nachnahme. The reason for this is to prevent the dosing pot becoming a deadleg and therefore a potential area for bacteriological contamination/corrosion. Generally dosing pots are fitted with lever valves. We recommend that these are just ‘cracked open’ so as to allow a degree of flow without starving the rest of the system of any water. Designers should now consider installing commissioning stations on dosing pot pipework and making a provision within their calculations as far as design flow rates are concerned.
http://www.conceptenvironmental.co.uk/wp-content/uploads/2016/10/f15fee3d-b15c-46c5-ac1e-8a402c7d1018.jpeg 300 154 PCollins http://demo.conceptes.co.uk/wp-content/uploads/2013/04/conceptes_logo1.jpg PCollins2016-10-02 18:45:232017-02-14 14:25:49Dosing pots on closed circuits